Replaces MS-5012, MS-5024, MS-5024UD, MS-2410B and the MS-5210UD
The new Fire-Lite MS-10UD-7, ten zone, conventional fire control panels have features normally found in more expensive addressable systems.
The MS-5UD-3(E) is a five-zone FACP (Fire Alarm Control Panel) and the MS-10UD-7(E) is a ten-zone FACP. These control panels provide reliable fire signaling protection for small to medium-sized commercial, industrial, and institutional buildings. Both panels include built-in communicators for Central Station Service and remote upload/download.
Each of these FACPs is compatible with System Sensor’s microprocessor-based i3 series detectors. These conventional smoke detectors can transmit a maintenance trouble signal to the FACP indicating the need for cleaning and a supervisory “freeze” signal when the ambient temperature falls below the detector rating. Additionally, both the MS-5UD-3 and MS-10UD-7 are compatible with conventional input devices such as two- and four-wire smoke detectors, pull stations, water flow devices, tamper switches, and other normally-open contact devices. Refer to Fire•Lite Device Compatibility Document for a complete listing of compatible devices.
Outputs include four NACs (Notification Appliance Circuits), three programmable Form-C relays (factory programmed for Alarm, Trouble, and Supervisory) and 24 VDC special application resettable and non resettable power outputs. The FACPs supervise all wiring, AC voltage, battery level and telephone line integrity.
Activation of a compatible smoke detector or any normally-open fire alarm initiating device will activate audible and visual signaling devices, illuminate an indicating LED, sound the piezo sounder at the FACP, activate the communicator and FACP alarm relay, and operate an optional module used to notify a remote station or initiate an auxiliary control function. The MS-5UD-3E and the MS-10UD-7E offer the same features as the MS-5UD-3 and MS-10UD-7 but allow connection to 220/240 VAC.
NOTE: Unless otherwise specified, the information in this data sheet applies to both the 110/120 VAC and the 220/240 VAC versions of these panels.
Five-zone, 24-volt Fire Alarm Control Panel (includes back box, FLPS-3 power supply, technical manual, and a frame & post operating instruction sheet).
MS-5UD-3E: Same as above with 240 VAC FLPS-3 power supply.
MS-10UD-7: Ten-zone, 24-volt Fire Alarm Control Panel (includes back box, FLPS-7 power supply, technical manual, and a frame & post operating instruction sheet).
MS-10UD-7E: Same as above with 240 VAC FLPS-7.
CAC-5X: Optional Style Z (Class A) Converter Module. Converts Style B (Class B) Notification Appliance Circuits to Style D (Class A) and Style Y (Class B). Connects to J2 on the MS- 5UD-3(E) and MS-10UD-7(E) main circuit board and to J7 on the MS-10UD-7(E).
NOTE: Two Class A Converter Modules are required for the ten-zone panel.
4XTMF: Transmitter module. Provides a supervised output for local energy municipal box transmitter and alarm and trouble reverse polarity. Includes a disable switch and disable trouble LED. A module jumper option allows the reverse polarity circuit to open with a system trouble condition if no alarm conditions exists. Mounts to the main circuit board connectors J4 and J5.
- ANN-80: Remote LCD Annunciator. Mimics the information displayed on the FACP’s LCD.
- ANN-LED: Mounts in the DP-51050 dress panel and provides three LEDs for each zone: Alarm, Trouble, and Supervisory.
- ANN-RLY: Relay module. Mounts inside the cabinet. Provides ten Form C relays.
- ANN-S/PG: Serial/parallel printer gateway. Provides a connection for a serial or parallel printer.
- ANN-I/O: Driver module. Provides connections to a user-supplied graphic annunciator.